think it was fitted by captain of a submarine (he missed his periscope) LOL
Keep getting e.mails saying please set your status !!
what do they mean cannot find it anywhere ?
my new years resolution is to make more money LOL way things are though think its another one that will fail !!!
accuracy of cylinder stats depend a lot on where on the cylinder they are located !
if to low the water will be hotter than stat setting (hot...
fairy does work tom same trick I used years ago. Cheap to ! also good as leak detector for gas LOL
To true Tom forgot that one, slap on the wrist to me !!
Better of with saniflo anyway.#
they are more reliable.
And they pump down 3/4" plastic (overflow) pipe.
So much easier to fit.
No to the heating pump idea it will rot in weeks (constantly changing water) and to weak anyway.
increasing the size of the cw tank (should be 50...
basically yes yes and no
could be shut
has the boiler been serviced recently.?
If not partially blocked waterways or flueways or the gas valve not set on the right pressure can cause...
you have answered your own question !!
either the stat or reciever (or both) is faulty.
first change the batteries in the stat just to alleviate...
its just a balancing (lockshield) valve take the top of and underneath will be either a screw or allen key type valve to open or close. But beware...
Yea pray and hope you got the diagnostic right and that the new board is not faulty.
Now where did I put them paracetamol HEADACHES
I agree with you tom shoving the blame around is NOT the thing to do. Most of us knew this problem would happen in feezing conditions and when...
Sludge, scale or corrosion or all three are prime candidates for this crime.
if its an old system it could be partially blocked pipes (cold feed or rads) and your pump is pumping over !!
Just a thought !
If its recent...
not really sure what your asking here !
template on wall,
From centre line of flue use spirit level across to outside wall. them measure lengh...
well done m8 problem solved
I would just re-instate it as it was !!
if you have to put in a bypass part L insists that it must be the automatic type (opens only when...
most domestic radiators are tapped 1/2" BSP
Separate names with a comma.