Discussion in 'Electricians' Talk' started by Kiev, Sep 15, 2020.
Just use one of these
I have used those a few times, Bazza, as a cable joint but I don't think they would accommodate a 16mm T&E and three 6mm2 T&E. Could be wrong but I can't see how it would work.
Looks like I got a bit carried away. Cable is more like 6mm than 16!
Pic of isolator
Not 6 mm, maybe 10mm.
What size fuse or MCB protects this circuit ?
And the earth conductor needs to be put into the terminal block with the other earth conductor, it's hanging loose !!!
Separate names with a comma.