Hi My mother needs some work done on a rental property for the electrical safety check. We use an electrician from the estate agents and have no doubts their work is fine, just wanted to check opinion as to if the quote was OK. Any thoughts would be appreciated. I assume any fittings will be basic, no luxury fittings or anything. £340 for: "There is an open Ring on the Neutral conductor, this has a risk of causing over heating the circuit and we need to find the loose connection or down grade the circuit from a 32A to 20A. The bathroom light needs replacing to a suitable IP rated light. There are single core conductors on show from the Shower circuit that need to be contained or rewired in the cupboard ADJ consumer unit. The Meter tail enters the Henly block where is was extended and has a section of single insulated cable that needs addressing. Where all the cables were extended for the consumer unit replacement, all the cable joins are wrapped up in tape, not contained in a proper enclosure and needs changing." Thank you in advance.